Here you’ll find examples of installations that have resolved common water quality issues in our region:
PFAS Removal Filtration Systems
Whole-Home Reverse Osmosis Filtration Systems
Carbon Filtration Systems
Radon-in-Water and Arsenic Removal Systems
Not sure of your problem or what solution you need?
Check out our Solutions page! It’s full of information about New England’s common water quality issues—and methods to resolve them.
Once we analyze the water test results, we do a site-inspection to determine (with you) the best location to install the proposed system in your home or business.
Twin 4-cubic feet Water Softeners with high-capacity sediment filter for lawn irrigation. System installed to remove high dissolved iron & sediment that was staining the landscape and clogging sprinkler heads.
From right: Radon-in-water removal system with pressure tank (blue) and 1 1/2 cubic feet high efficiency Water Softener. 20″ graded density sediment filter behind softener.
Twin (redundant) arsenic removal system with test ports and high-efficiency 1.5 cubic-feet Water Softener with ‘big blue” graded density 5-micron sediment filter. Also installed a reverse osmosis purification system (on wall with 3 white housings with white storage tank) feeding a separate faucet upstairs at the kitchen sink.
New construction. 2 cubic-feet combination water softener/carbon filtration system for public water supply with hard water and very noticeable chlorine taste & smell. Accompanied by large capacity sediment filter for this large home.
Twin water softener with high-capacity sediment filter to treat water being used in a manufacturing environment.
Large-capacity sediment and activated carbon filters for this new construction, large home to remove heavy sediment as well as Trihalomethanes reported in the water supply.
Very-large-capacity twin water softeners installed in regional hospital to protect the mechanical systems from hardness in the water supply.
2 cubic-feet high-efficiency Water Softener with large-capacity sediment filter.
Whole-house reverse osmosis filtration system installed to desalinate private well on coastal property experiencing saltwater intrusion.
Large tank of activated carbon to remove bad taste & odor from the feed water supplying this local craft brewery.
1.5 cubic feet Water Softener with PFAS removal system (shorter black tank with green illumination) and 20″ “big blue” 5-micron graded density sediment pre-filter.
1 cubic-foot, high-efficiency Water Softener with 20-inch, “Big Blue” graded density 5-micron sediment filter and activated carbon filter. Installed on public water supply with hard water, sediment & heavy chlorine.
Reverse Osmosis Purification System installed in basement with line running up to a dedicated faucet in Kitchen. Twin 20″ 5 micron graded density sediment filter and Activated carbon filter to improve all incoming water at point of entry.
a 20″ 5 micron graded density pre-filter. System removing hardness, iron,
neutralizing corrosive, low pH and eliminating strong rotten egg smell.
Twin arsenic removal system with testing port, with Ozone generating system to eliminate very strong odor from the water. A 5 micron graded density Sediment pre-filter installed as well, per standard.