When sizing a commercial water softener system, doing the math and getting a reasonable forecast of volume demand in gallons is critical to determining the proper size of the system. Water softening resin has a finite amount of water that it can soften before it needs to go into a backwash (or self cleaning) cycle to clean the resin beads for continued softening. Additionally, determining the size of the brine tank for softener salt storage is also very important to keep the tank filling requirements at a reasonable level for the personnel maintaining this.
Space available for the equipment is another important consideration. To avoid a long piping run to and from the system, a good location needs to be selected. Additionally, any space restrictions will need to taken into consideration when sizing both the softener and brine tank sizes.
WHEN TWO COMMERCIAL WATER SOFTENERS ARE NEEDED
In a hospital setting or other setting where water is being used essentially 24 hours per day, a back up softener may be required. The main reason for this is when one softener goes into its backwash cycle, the second softener will be able to provide a steady supply of softened water to the facility. Without this backup, unconditioned water will be pulled through the system while the softener is in the backwash cycle. In the photo at the top of the page, this system is feeding make-up water to the boiler. It has to be clean water 24 hours a day.
For more on how a water softener works, see the link at Water Softening.
H2O Care, Inc. is an established water filtration and testing firm, founded in 1989. Offices are located in Middleton and Stow, MA. Reach us at [email protected] or 800-539-1100. See articles published by us in Water Technology Magazines on regional water quality issues at https://publications/.